Version: 3.27r1 2012-07-13
BUG: Current input at an IOX (Control of the Easy-Connect-Kit) results in different ADC counts than current
input at an Seccua Control Pro UFH (Virex and Phoenix control). Therefore the ADC counts from the IOX received via
CAN have to be multiplied with a correction factor.
I. e. the IOX ADC counts have to be multiplied with
((120 Ohm / 160 Ohm) / (5000 mV / 4096 mV)) in order to get
corresponding UFH ADC counts.
This bug fix implements that IOX UFH ADC counts conversion factor.
Seccua Control Pro (Virex and Phoenix) shipped after 1. Jan 2012 (large data-log) can be upgraded to firmware-version 3.27r1
PC Software 3.20r0 is required to connect to this firmware version.